CALL For Installation ☎︎7003965656
Product Installation is Very Easy just Follow the given Instruction below:
1.Unbox the Product & the Instruction Manual.
- Get Familiar with the Product. Big BLACK Switch on the left side (For Auto & Manual Operation). On the top of Product there are 6 Sensor wires for Sensor Probe Connection and remaining 3 Wires for Pump Automatic Operation Connection to the pump starter panel. Product Installation Procedure:
1.Cut off the power supply for pump starter / switch prior to start the installation.
- Hang the Fully Automatic Pump On-Off Controller device near Pump Starter / Switch.
- Connect P+ with Phase, Then Pump+ connect with Pump +ve power input supply towards Pump. Then N(-) with Neutral.
FOR OHT TANK SENSOR CONNECTION
Fix the Sensor Probe inside OHT (Over Head Tank) in 3 different Levels, to fix OHT High sensor probe 5 Inches below overflow pipe. OHT Low sensor probe 10 Inches above from bottom and OHT Ground sensor probe just above 8 Inches from tank bottom.
FOR RESERVOIR/UNDERGROUND TANK SENSOR CONNECTION
Fix the Sensor Probe inside Reservoir Tank in 3 Different Levels, To fix RES GROUND sensor probe 4 Inches above suction pipe, RES LOW sensor probe 6 Inches above suction pipe & RES HIGH sensor probe 10 Inches above suction pipe.
Bring all 6 sensor wires from OHT &RES Tank (which is connected to the sensor probes as shown in diagram) & connect accordingly. & before starting main switch, be sure AUTO/MANUAL Switch should be in auto position.
(NOTE:- KEEP PUMP STARTER/SWITCH ‘ON’ ALL THE TIME WHEN WATER PUMP CONTROLLER IS IN AUTO POSITION) & MANUAL SWITCH IS FOR EMERGENCY PURPOSE ONLY.
IF YOU FOUND ANY DIFFICULTY DURING INSTALLATION, FEEL FREE TO CONTACT OUR DEALER, DISTRIBUTOR, RESELLER OR COMPANY REPRESENTATIVE.
IMPORTANT NOTE:- It is advised by the company to contact us prior to Installation of Device. Fully Automatic Pump On-Off Controller Installation will vary for different starter panel.